30 CFR § 75.801
The grounding resistor, where required, shall be of the proper ohmic value to
limit the voltage drop in the grounding circuit external to the resistor to
not more than 100 volts under fault conditions. The grounding resistor shall
be rated for maximum fault current continuously and insulated from ground for
a voltage equal to the phase-to-phase voltage of the system.